The American Architectural Manufacturers Association (AAMA) released AAMA , a voluntary specification for field testing of newly. Newly Installed Fenestration Products” and. AAMA , “Voluntary Specification for Field Testing of Newly Installed. Storefronts, Curtain Walls and Sloped. AAMA and documents, designed for field testing of newly installed fenestration products. The aforementioned. AAMA documents were often.
|Published (Last):||13 June 2005|
|PDF File Size:||13.2 Mb|
|ePub File Size:||16.46 Mb|
|Price:||Free* [*Free Regsitration Required]|
Water Penetration Field Testing
aam See our AAMA page for additional information. Search by product code or category or leave the product code field blank to see a list of all AAMA publications. Procedure B is a cyclic static air pressure difference.
There are two different procedures listed for the test method. Begin your publication search by entering information into the fields below.
Member discount will be reflected after successful login to the Checkout process. The AAMA can be utilized if the project requires investigative testing.
AAMA Water Spray Testing
See our AAMA page for additional information if your project requires to test for the rated air leakage or rated water penetration performance. Analyzing the data and establishing a cause and effect relationship between wall characteristics and the observed leakage.
This field check is not appropriate for testing operable components.
The AAMA was first released in and has had many changes over the years. Which would be referred to as quality assurance testing.
AAMA Combined Air & Water Testing | BETechnologies Ireland
The purpose of this voluntary guideline is to recreate leaks that are known to occur. There are no previous editions. This field check procedure is only intended to evaluate joints, gaskets and sealant details in the glazing which are designed to remain permanently closed and water tight.
This differs greatly from the AAMA and AAMA field testing procedures that are intended for evaluating newly installed fenestration products or quality assurance testing. It can only be utilized prior to the issuance of the building occupancy permit and no later than six months after the installation of the fenestration product.
This test method exclusively utilizes a uniform static air pressure zama. ASTM E references the following documents: SITC determines what procedure to utilize based on the laboratory testing results. The main objective of forensic water testing is to identify the leak paths through the simulation of the weather events that produced the reported leakage.
This specification establishes the requirements for test specimens, apparatus, sampling, test procedures and test reports to be used in evaluating the performance of newly installed storefronts, curtain walls and sloped glazing systems.
ASTM states the field test may also be made after the building is completed and in service to determine whether or not reported leakage problems are due to the failure of the installed assemblies. This specification provides a guide which can be used to evaluate the installed performance of storefronts, curtain walls and sloped glazing systems for resistance to awma penetration under controllable and reproducible wind driven rain conditions.
The AAMA is the proper test method for field testing of storefronts, curtain walls and sloped glazing for air leakage and water penetration resistance performance. The most current edition is the AAMA These systems shall be tested per the AAMA This standard is utilized for either field quality assurance testing 053-08 forensic testing.
Specifically excluded from this field check method is the testing of operable components such as operable window and doors. The testing procedure outlined in the AAMA The AAMA is the first edition of this voluntary guideline. Specifically excluded from this specification are windows, glass doors and skylights. Read more about 503–08 our customers have to say This starts with a clearly defined sequence of activities that SITC follows during a investigation: Procedure A is a uniform static air pressure difference.
American Architectural Aa,a Association. Please contact AAMA for assistance, as needed. Please read our simple purchasing instructions first aamx ensure a smooth transaction.
AAMA Water Spray Testing
This specification is for quality assurance testing only. The diagnostic field water check is utilized for installed storefronts, curtain walls and sloped glazing systems only. The AAMA describes steps for calculating the approximate differential air pressures the specimens experienced during actual wind driven rain events.
This field water check method is not intended to test the rated or specified water performance representative of a wind driven rain event.
The evaluation of the design concept to determine if any water resistance performance requirements were specified for the wall. SITC utilizes isolation techniques to assist in identifying the source or sources of the reported water leakage.